EWYQ160F-XS | EWYQ190F-XS | EWYQ210F-XS | EWYQ230F-XS | EWYQ310F-XS | EWYQ340F-XS | EWYQ380F-XS | EWYQ400F-XS | EWYQ430F-XS | EWYQ510F-XS | EWYQ570F-XS | EWYQ630F-XS | ||||
---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|

Cooling capacity | Nom. | kW | 164 (1) | 184 (1) | 205 (1) | 231 (1) | 304 (1) | 335 (1) | 376 (1) | 401 (1) | 427 (1) | 502 (1) | 565 (1) | 624.4 | |

Heating capacity | Nom. | kW | 173 (2) | 197 (2) | 227 (2) | 254 (2) | 329 (2) | 362 (2) | 404 (2) | 429 (2) | 463 (2) | 535 (2) | 607 (2) | ||

Capacity control | Method | Step | Step | Step | Step | Step | Step | Step | Step | Step | Step | Step | Staged | ||

Minimum capacity | % | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 25.0 | 17.0 | 17.0 | 17 | ||

Power input | Cooling | Nom. | kW | 57.6 (1) | 63.3 (1) | 70.3 (1) | 79.3 (1) | 102 (1) | 114 (1) | 129 (1) | 138 (1) | 145 (1) | 172 (1) | 195 (1) | 214.4 |

Heating | Nom. | kW | 54.0 (2) | 61.6 (2) | 70.5 (2) | 79.2 (2) | 101 (2) | 113 (2) | 126 (2) | 133 (2) | 140 (2) | 167 (2) | 190 (2) | ||

EER | 2.84 (1) | 2.91 (1) | 2.92 (1) | 2.92 (1) | 2.99 (1) | 2.93 (1) | 2.91 (1) | 2.90 (1) | 2.94 (1) | 2.92 (1) | 2.90 (1) | 2.912 | |||

COP | 3.20 (2) | 3.20 (2) | 3.22 (2) | 3.21 (2) | 3.24 (2) | 3.21 (2) | 3.21 (2) | 3.23 (2) | 3.30 (2) | 3.21 (2) | 3.20 (2) | ||||

ESEER | 3.73 | 3.89 | 3.81 | 3.71 | 4.07 | 4.19 | 3.99 | 3.96 | 4.14 | 4.20 | 3.98 | 4.06 | |||

Dimensions | Unit | Depth | mm | 4,370 | 4,370 | 5,270 | 5,270 | 4,125 | 4,125 | 4,125 | 5,025 | 5,025 | 5,925 | 5,925 | 6,825 |

Height | mm | 2,270 | 2,270 | 2,270 | 2,270 | 2,220 | 2,220 | 2,220 | 2,220 | 2,220 | 2,220 | 2,220 | 2,220 | ||

Width | mm | 1,200 | 1,200 | 1,200 | 1,200 | 2,258 | 2,258 | 2,258 | 2,258 | 2,258 | 2,258 | 2,258 | 2,258 | ||

Weight | Operation weight | kg | 1,470 | 1,890 | 2,340 | 2,390 | 2,980 | 2,990 | 3,000 | 3,840 | 3,850 | 4,370 | 4,400 | 4,780 | |

Unit | kg | 1,430 | 1,850 | 2,300 | 2,350 | 2,900 | 2,910 | 2,920 | 3,730 | 3,750 | 4,250 | 4,280 | 4,670 | ||

Water heat exchanger | Type | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | Plate heat exchanger | ||

Water volume | l | 18 | 18 | 18 | 18 | 44 | 44 | 44 | 60 | 60 | 70 | 70 | 70 | ||

Air heat exchanger | Type | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type with integral subcooler | High efficiency fin and tube type | ||

Fan | Air flow rate | Nom. | l/s | 22,577 | 21,593 | 26,992 | 26,992 | 43,187 | 43,187 | 43,187 | 55,213 | 53,983 | 64,780 | 64,780 | 75,577 |

Speed | rpm | 900 | 900 | 900 | 900 | 900 | 900 | 900 | 900 | 900 | 900 | 900 | 900 | ||

Compressor | Quantity | 4 | 4 | 4 | 4 | 4 | 4 | 4 | 4 | 4 | 6 | 6 | 6 | ||

Type | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Scroll compressor | Driven vapour compression | |||

Sound power level | Cooling | Nom. | dBA | 92 | 94 | 95 | 95 | 97 | 97 | 98 | 99 | 99 | 99 | 100 | 100 |

Sound pressure level | Cooling | Nom. | dBA | 72 (5) | 74 (5) | 75 (5) | 76 (5) | 77 (5) | 77 (5) | 78 (5) | 78 (5) | 79 (5) | 79 (5) | 79 (5) | 80 |

Refrigerant | Type | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | ||

GWP | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,088 | |||

Circuits | Quantity | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | 2 | ||

Charge | Per circuit | kg | 16.0 | 20.0 | 20.0 | 24.0 | 35.0 | 36.0 | 35.0 | 46.0 | 46.0 | 55.0 | 52.5 | ||

Per circuit | TCO2Eq | 33.4 | 41.8 | 41.8 | 50.1 | 73.1 | 75.2 | 73.1 | 96.0 | 96.0 | 114.8 | 109.6 | 142.0 | ||

Refrigerant circuit | Charge | kg | 136 | ||||||||||||

Power supply | Phase | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | ||

Frequency | Hz | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | ||

Voltage | V | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | ||

Compressor | Starting method | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | Direct on line | ||

Notes | (1) - Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | (1) - Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | (1) - Cooling: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation. | ||||||||||||

(2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | (2) - Heating: air exchanger 7.0 - 90%°C; water exchanger 40.0/45.0, unit at full load operation. | ||||

(3) - SCOP is based on the following conditions: Tbivalent +2°C, Tdesign -10°C, Average ambient conditions, Ref. EN14825. | (3) - SCOP is based on the following conditions: Tbivalent +2°C, Tdesign -10°C, Average ambient conditions, Ref. EN14825. | (3) - SCOP is based on the following conditions: Tbivalent +2°C, Tdesign -10°C, Average ambient conditions, Ref. EN14825. | |||||||||||||

(4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | (4) - Fluid: Water | ||||

(5) - Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | (5) - Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | (5) - Sound pressure levels are measured at entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C; full load operation; Standard: ISO3744 | |||||||||||||

(6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | (6) - Allowed voltage tolerance ± 10%. Voltage unbalance between phases must be within ± 3%. | ||||

(7) - Maximum starting current: starting current of biggest compressor + current of the other compressors at maximum load + fans current at maximum load. In case of inverter driven units, no inrush current at start up is experienced. | (7) - Maximum starting current: starting current of biggest compressor + current of the other compressors at maximum load + fans current at maximum load. In case of inverter driven units, no inrush current at start up is experienced. | (7) - Maximum starting current: starting current of biggest compressor + current of the other compressors at maximum load + fans current at maximum load. In case of inverter driven units, no inrush current at start up is experienced. | |||||||||||||

(8) - Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | (8) - Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | (8) - Nominal current in cooling mode: entering evaporator water temp. 12°C; leaving evaporator water temp. 7°C; ambient air temp. 35°C. Compressor + fans current. | |||||||||||||

(9) - Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | (9) - Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | (9) - Maximum running current is based on max compressor absorbed current in its envelope and max fans absorbed current | |||||||||||||

(10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | (10) - Maximum unit current for wires sizing is based on minimum allowed voltage. | ||||

(11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | (11) - Maximum current for wires sizing: (compressors full load ampere + fans current) x 1.1 | ||||

(12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | (12) - For more details, see operation range drawing | ||||

(13) - Equipment contains fluorinated greenhouse gases. Actual refrigerant charge depends on the final unit construction, details can be found on the unit labels. | (13) - Equipment contains fluorinated greenhouse gases. Actual refrigerant charge depends on the final unit construction, details can be found on the unit labels. | (13) - Equipment contains fluorinated greenhouse gases. Actual refrigerant charge depends on the final unit construction, details can be found on the unit labels. |